BOSTON, GA REVIEWS
Benson’s Heating & Air Conditioning promises customer service that exceeds the expectations of Boston GA residents.
Call us now at: 850-562-3132. We’d love the opportunity to earn your business as we have with your neighbors in Boston GA.
for Boston, GA
CONNER - Boston, GA
Questions asked regarding specific services were answered.
Very Professional Service
CONNER - Boston, GA
Answered all questions regarding service!
very professional and very helpful!
Mrs. Janice Conner - Boston, GA
We are pleased with the outstanding service from your staff.
Conscientious, Timely, Communicated prior to Coming
Walt - Boston, GA
Brandon Graham is personable and a good rep for Benson. We were unaware our surge protection was from the house in and not on the outside. He installed the appropriate surge protection for the units on the outside. As well, he called both days to let us know he was on the way. We are extremely satisfied with the service.
White Rental - Boston, GA
Simply the best service ever! Very nice technicians and very knowledgeable too! Completely happy with Benson Heating and Air Conditioning
Today we performed a Silver level summer tune up on your Tappan heat pump unit. Everything is working properly at this time. Thank you for your business today. Tallahassee, Florida
Performed a tune up on a nordyne heat pump in Boston
Performed a tune up on a Lennox air conditioner in Boston ga
Performed a diamond level tune up on all the equipment. Tested system operations, component amperages, capacitor ratings, cleared all the drain lines, changed all the filters on the property, checked and replaced batteries as needed in the thermostats, dusted the return grills, and cleaned the condensers. Found the breakfast nook system was not working due to a faulty dual run capacitor. We replaced the capacitor and now all systems are working at this time. Found some weak capacitors and pitted motor starters that I emailed you a estimate to replace them before they go out to keep the systems from being downed, and I found the house and garage air handlers and duct work needs to be cleaned. I emailed you an estimate to have the house and garage air handlers and duct work cleaned. I could not find Ben or the house keeper to sign invoice. Please feel free to call me with any questions, Lee Costa 519-4251. Billable
Performed a tune up on a Lennox heat pump in Boston
No one there. Need to reschedule.
Tune up on Lennox unit
Completed Mainteniamce On Carrier Units
Replaced two compressors, a leaking evaporator coil, a cracked primary pan, a weak run capacitor, replaced seven UV bulbs, and cleared seven drain lines. All seven Carrier air conditioners are working properly at this time in Boston, GA.
Did silver level maintenance on two gas furnace. Carbon monoxide:000ppm.