Meigs, GA Heating and Air Conditioning
Benson’s Heating & Air Conditioning is the top choice in Meigs, GA and the surrounding areas for heating and air conditioning services! Call us first for your HVAC repair, installation and tune-up needs. We also provide exceptional indoor air quality services.
Our customers know! Read some of our reviews below from homeowners and businesses in the Meigs, GA area.
for Meigs, GA
Our Reviews by City
WELDON - Meigs, GA
Awesome, timely response. Great service!
WELDON - Meigs, GA
Performed deep cleaning on two mini split heads and one condenser. Also replaced the 8790 Lennox filter in the main house.
Performed a winter time tune up on 3 Goodman, 1 Lennox, and 1 grand aire heat pump, 1 Lennox package unit, and 2 daikin mini split systems in Meigs, Ga.
Performed a winter time tune up on two Lennox, two Goodman, and one grand heat pump. And one Lennox heat pump package unit in Meigs, Ga.
Found the control board in the condenser to be shorted out and the fan motor to be faulty. System is down. I will check availability status Monday morning. 8/30/19 Replaced condenser fan motor & board. System is working properly at this time.
Found unit leaking at the evaporator coil. Checked pressures. Added 2 pounds of refrigerant to get it cooling. Ordered coil, valve, and drier. Please schedule once parts come in for either me and nuno or the coil crew to make repairs. Unit is in a attic. Will take 6 hours plus drive time. 8/30/19 Replaced Lennox evap coil, pressure tested to ensure there are no leaks, pulled vacuum to 500 microns. The system is working properly at this time.
The blower motor failed and was not allowing the system to cool or heat. I replaced the blower motor and tested the system in cool and heat modes. The system is operating properly at this time.
Performed a diamond level second visit tune up on 7 systems. Testing system operations, component amperages, capacitor ratings, cleared the drain lines, changed the high media filter in the main house,changed the UV bulbs in the main house, washed all the filters in the barn, checked the filters in the guest house, dusted the return grills, and cleaned the condensers outside. In the guest house sun room I found the system not cooling due to a faulty blower motor booster in the air handler. I replaced it with a new one. All the systems are now cooling properly at this time. Billable.