Perry, FL Heating and Air Conditioning
Since 1981, Benson’s Heating & Air Conditioning has provided exceptional AC and heating repair, installation and maintenance services to the residents of Perry, FL. Our local professional team of technicians has the right experience and knowledge for any heating and cooling job you need. And better yet? Our open, honest way of doing business will help you choose to partner with us again and again.
Your neighbors in Perry, FL consider us their go-to HVAC contractor. Check out some of their reviews below to see why!
for Perry, FL
Our Reviews by City
Today we performed a Silver level summer time tune up on your Tappan heat pump unit, everything is working properly at this time. Thank you for your business. Tallahassee Fl
Today I performed a winter time tune up on your Tappan heat pump unit. Everything is working properly at this time. Thank you for your business. Perry, Fl
Today we performed a Silver level summer tune up on your American Standard heat pump unit. The contactor on the condenser is starting to wear out and we also recommend having the duct work cleaned to provide better air flow. Everything else is working properly at this time. Thank you for your business. Perry Fl
I performed a summertime tune up on a tappan heat pump in perry.
I performed a Silver level visit tune up on the equipment. Testing system operations, component amperages, capacitor ratings, cleared the drain line, checked the filter, cleaned the condenser outside, and checked the thermostat. The system is working properly at this time. Thank you for your business today. Perry, Florida.
Today we performed a commercial winter tune up on your Daikin heat pump mini split unit, everything is working properly at this time. Thank you for your business. Perry Fl
Performed commercial maintenance as agreed. Cleared drain line and washed filters. Sprayed coils on outside unit and cleaned them. Tested and amped unit. Unit is operating properly at this time.
Preformed Silver Level maintenance 1st visit on one heat pump system. I checked all parts and operations in heat mode. The (1) 20x25x1 filter was good and the drain line was cleared. The customer was emailed a copy of the maintenance report. Overall the system is heating properly at this time.
Performed a maintenance on a Tappan air conditioner in Perry FL
Completed Maintenance On Tappan Unit